Table of Exhibits Approval Current Revision Introduction About PJM Manuals About This Manual Using This Manual Section 1: Generator Markets and Operations 1. 1 Generator Interconnection Process: Markets and Operations Phase 1.
2 Generator Commercial Naming Convention Section 2: Responsibilities of Generation Owners 2. 1 Generator Owners Responsibilities reference to PJM Manual 14D Welcome to the PJM Manual for Generation and Transmission Interconnection Facility Construction. In this Section you will find: Generation and Transmission Interconnection Facility Construction. In this section you will find an overview of the different types of agreements that are an This PJM Region Transmission Planning Process Manual consists of two sections and related attachments.
All sections and attachments are listed in the Table of Contents. Attachment H, PJM Generation and Transmission Interconnection Planning Process Flow Diagram, revised for consistency with Manual M14AC. Attachment M, Manual Changes: M11, M14D, M15 July 2, 2013 The Markets and Reliability Committee Thursday approved changes to Manuals 11 and 14D, while the Members Committee approved changes to Manual Manual 14D: Generator Operational Requirements Revision 18, Effective Date: Power System Coordination Department Reserve Manual 14D: Generator Operational Requirements Table of Exhibits PJM 2015 Revision 37, Effective Date: ii PJM Manual 14D: Generator Operational Requirements Attachment D: PJM Generating Unit Reactive Capability Curve Specification and Reporting Procedures.
113 Attachment E: PJM Generator and Synchronous Condenser PJM Manual 14D: Generator Operational Requirements 14. requirements. Requirements. PJM. Data. Operational. markets. The PJM Region Transmission Planning Process Manual Pjm manual 14d attachment exploration one of the PJM manuals in the PJM Regional Transmission Expansion group.
This manual focuses on the process for Attachment D: PJM Generating Unit Reactive Capability Curve Specification and The PJM Manuals are the instructions, rules, procedures, and guidelines established by PJM for the operation, planning, and accounting requirements of the PJM Control Area and Manual 14D: Generator Operational Requirements Schedule 2 of PJMs Tariff, which covers Reactive Service, provides that PJM will compensate owners of generation and nongeneration resources for maintaining the capability to provide reactive power to PJM.
Specifically, Schedule 2 states that, for 13 See PJM Manual 14D, Attachment E, Sample Forms, page 118. The The Markets and Reliability Committee heard first reading last week on the following PJM manual changes.
Members will be asked to endorse the changes at the MRCs next meeting.